-----BEGIN PGP SIGNED MESSAGE-----
AUSCERT External Security Bulletin Redistribution
Advisory (icsa-20-161-02) Mitsubishi Electric MELSEC iQ-R series
10 June 2020
AusCERT Security Bulletin Summary
Product: Mitsubishi Electric MELSEC iQ-R series
Operating System: Network Appliance
Impact/Access: Denial of Service -- Remote/Unauthenticated
CVE Names: CVE-2020-13238
- --------------------------BEGIN INCLUDED TEXT--------------------
ICS Advisory (ICSA-20-161-02)
Mitsubishi Electric MELSEC iQ-R series
Original release date: June 09, 2020
All information products included in https://us-cert.gov/ics are provided"as
is" for informational purposes only. The Department of Homeland Security (DHS)
does not provide any warranties of any kind regarding any information contained
within. DHS does not endorse any commercial product or service, referenced in
this product or otherwise. Further dissemination of this product is governed by
the Traffic Light Protocol (TLP) marking in the header. For more information
about TLP, see https://www.us-cert.gov/tlp/ .
1. EXECUTIVE SUMMARY
o CVSS v3 5.3
o ATTENTION: Exploitable remotely/low skill level to exploit
o Vendor: Mitsubishi Electric
o Equipment: MELSEC iQ-R series
o Vulnerability: Resource Exhaustion
2. RISK EVALUATION
Successful exploitation of this vulnerability could cause the Ethernet port to
enter a denial-of-service condition.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
Mitsubishi Electric reports that the vulnerability affects the following MELSEC
iQ-R series modules:
o R04/08/16/32/120CPU, R04/08/16/32/120ENCPU: Firmware Versions 39 or earlier
o R00/01/02CPU: Firmware Versions 7 or earlier
o R08/16/32/120SFCPU: Firmware Versions 20 or earlier
o R08/16/32/120PCPU: All versions
o R08/16/32/120PSFCPU: All versions
o RJ71EN71: All versions
3.2 VULNERABILITY OVERVIEW
3.2.1 UNCONTROLLED RESOURCE CONSUMPTION ('RESOURCE EXHAUSTION') CWE-400
Uncontrolled resource consumption can be caused when an attacker sends a large
amount of specially crafted packets in bursts over a short period.
CVE-2020-13238 has been assigned to this vulnerability. A CVSS v3 base score of
5.3 has been calculated; the CVSS vector string is ( AV:N/AC:L/PR:N/UI:N/S:U/
o CRITICAL INFRASTRUCTURE SECTORS: Critical Manufacturing
o COUNTRIES/AREAS DEPLOYED: Worldwide
o COMPANY HEADQUARTERS LOCATION: Japan
Yossi Reuven of SCADAfence reported this vulnerability to Mitsubishi Electric.
Mitsubishi Electric recommends users of the affected devices mitigate impact of
this vulnerability by using firewalls to block access from unreliable networks
CISA recommends users take defensive measures to minimize the risk of
exploitation of this vulnerability. Specifically, users should:
o Use secure methods when remote access is required, such as virtual private
networks (VPNs), recognizing that VPNs may have vulnerabilities and should
be updated to the most current version available. Also recognize that VPN
is only as secure as the connected devices.
CISA reminds organizations to perform proper impact analysis and risk
assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices
on the ICS webpage on us-cert.gov . Several recommended practices are available
for reading and download, including Improving Industrial Control Systems
Cybersecurity with Defense-in-Depth Strategies .
Additional mitigation guidance and recommended practices are publicly available
on the ICS webpage on us-cert.gov in the Technical Information Paper,
ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation
Organizations observing any suspected malicious activity should follow their
established internal procedures and report their findings to CISA for tracking
and correlation against other incidents.
No known public exploits specifically target this vulnerability.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by
choosing one of the links below to provide feedback about this product.
- --------------------------END INCLUDED TEXT--------------------
You have received this e-mail bulletin as a result of your organisation's
registration with AusCERT. The mailing list you are subscribed to is
maintained within your organisation, so if you do not wish to continue
receiving these bulletins you should contact your local IT manager. If
you do not know who that is, please send an email to email@example.com
and we will forward your request to the appropriate person.
NOTE: Third Party Rights
This security bulletin is provided as a service to AusCERT's members. As
AusCERT did not write the document quoted above, AusCERT has had no control
over its content. The decision to follow or act on information or advice
contained in this security bulletin is the responsibility of each user or
organisation, and should be considered in accordance with your organisation's
site policies and procedures. AusCERT takes no responsibility for consequences
which may arise from following or acting on information or advice contained in
this security bulletin.
NOTE: This is only the original release of the security bulletin. It may
not be updated when updates to the original are made. If downloading at
a later date, it is recommended that the bulletin is retrieved directly
from the author's website to ensure that the information is still current.
Contact information for the authors of the original document is included
in the Security Bulletin above. If you have any questions or need further
information, please contact them directly.
Previous advisories and external security bulletins can be retrieved from:
Australian Computer Emergency Response Team
The University of Queensland
Internet Email: firstname.lastname@example.org
Facsimile: (07) 3365 7031
Telephone: (07) 3365 4417 (International: +61 7 3365 4417)
AusCERT personnel answer during Queensland business hours
which are GMT+10:00 (AEST).
On call after hours for member emergencies only.
-----BEGIN PGP SIGNATURE-----
-----END PGP SIGNATURE-----