-----BEGIN PGP SIGNED MESSAGE-----
AUSCERT External Security Bulletin Redistribution
Advisory (icsa-20-014-06) OSIsoft PI Vision
16 January 2020
AusCERT Security Bulletin Summary
Product: OSIsoft PI Vision
Operating System: Network Appliance
Impact/Access: Cross-site Request Forgery -- Remote with User Interaction
Cross-site Scripting -- Remote with User Interaction
Access Confidential Data -- Existing Account
CVE Names: CVE-2019-18275 CVE-2019-18273 CVE-2019-18271
- --------------------------BEGIN INCLUDED TEXT--------------------
ICS Advisory (ICSA-20-014-06)
OSIsoft PI Vision
Original release date: January 14, 2020
All information products included in http://ics-cert.us-cert.gov are
provided"as is" for informational purposes only. The Department of Homeland
Security (DHS) does not provide any warranties of any kind regarding any
information contained within. DHS does not endorse any commercial product or
service, referenced in this product or otherwise. Further dissemination of this
product is governed by the Traffic Light Protocol (TLP) marking in the header.
For more information about TLP, see http://www.us-cert.gov/tlp/ .
1. EXECUTIVE SUMMARY
o CVSS v3 7.1
o ATTENTION: Exploitable remotely/low skill level to exploit
o Vendor: OSIsoft LLC
o Equipment: PI Vision
o Vulnerabilities: Improper Access Control, Cross-site Request Forgery
(CSRF), Cross-site Scripting, Inclusion of Sensitive Information in Log
2. RISK EVALUATION
Successful exploitation of these vulnerabilities may allow disclosure of
sensitive information and limit the availability of the system.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of PI Vision, a visualization tool, are affected:
o CVE-2019-18275 and CVE-2019-18271 : All versions of PI Vision prior to 2019
o CVE-2019-18273 : PI Vision 2017 R2 and PI Vision 2017 R2 SP1
o CVE-2019-18244 : PI Vision 2017 R2, PI Vision 2017 R2 SP1, PI Vision 2019
3.2 VULNERABILITY OVERVIEW
3.2.1 IMPROPER ACCESS CONTROL CWE-284
The affected product is vulnerable to an improper access control, which may
return unauthorized tag data when viewing analysis data reference attributes.
CVE-2019-18275 has been assigned to this vulnerability. A CVSS v3 base score of
6.5 has been calculated; the CVSS vector string is ( AV:N/AC:L/PR:L/UI:N/S:U/
3.2.2 CROSS-SITE REQUEST FORGERY (CSRF) CWE-352
The affected product is vulnerable to a cross-site request forgery that may be
introduced on the PI Vision administration site.
CVE-2019-18271 has been assigned to this vulnerability. A CVSS v3 base score of
7.1 has been calculated; the CVSS vector string is ( AV:N/AC:L/PR:N/UI:R/S:U/
3.2.3 IMPROPER NEUTRALIZATION OF INPUT DURING WEB PAGE GENERATION ('CROSS-SITE
The affected product is vulnerable to cross-site scripting, which may allow
invalid input to be introduced.
CVE-2019-18273 has been assigned to this vulnerability. A CVSS v3 base score of
6.4 has been calculated; the CVSS vector string is ( AV:N/AC:H/PR:H/UI:R/S:U/
3.2.4 INCLUSION OF SENSITIVE INFORMATION IN LOG FILES CWE-532
The affected product records the service account password in the installation
log files when a non-default service account and password are specified during
installation or upgrade.
CVE-2019-18244 has been assigned to this vulnerability. A CVSS v3 base score of
5.1 has been calculated; the CVSS vector string is ( AV:L/AC:H/PR:N/UI:N/S:U/
o CRITICAL INFRASTRUCTURE SECTORS: Multiple
o COUNTRIES/AREAS DEPLOYED: Worldwide
o COMPANY HEADQUARTERS LOCATION: United States
OSIsoft reported this self-discovered issue to CISA.
OSIsoft recommends users upgrade to PI Vision 2019 to resolve these issues.
Additionally, OSIsoft recommends the following defensive measures:
CVE-2019-18275 : If upgrade is not an option, administrators should regularly
audit the AF hierarchy to ensure that there are no unexpected or unknown
elements/attributes. It is recommended that security on elements in AF be
configured and enforced in addition to configuring PI point security.
Potential unauthorized viewing of PI System data due to this issue is limited
to permissions granted to the PI Vision Application Pool Identity. Configure a
dedicated identity mapping for PI Vision servers and manage permissions in
accordance with a data classification policy.
CVE-2019-18271 and CVE-2019-18273 : All access to the AF Server is protected by
Windows authentication, so the modifications to AF data items required by an
attacker would have to be performed by a user with write access to either the
AF hierarchy or templates. Periodic review of AF Server permissions to ensure
only intended users are granted write access to elements, element templates,
event frame templates, and databases and servers configured on the PI Vision
admin site is a good practice to reduce exposure.
Similarly, which data items are available to PI Vision is controlled by the PI
Vision Administrators through the Administrative site. Only add data sources to
PI Vision that you can verify as legitimate with appropriate access control
CVE-2019-18244 : Provision and use domain Group Managed Service Accounts or use
the default NetworkService account to run PI Vision AppPools-there is no
exposure to this vulnerability when using either of these account types.
To limit exposure if a standard domain account is used to run PI Vision
AppPools, remove the password entry from the setup log files immediately. The
vulnerable log file is %pihome%\dat\SetupPIVision.log
For more information and workaround details for these vulnerabilities, please
refer to OSIsoft's Security Bulletin (registration required): OSIsoft releases
security update in PI Vision 2019
CISA recommends users take defensive measures to minimize the risk of
exploitation of this vulnerability. Specifically, users should:
o Minimize network exposure for all control system devices and/or systems,
and ensure that they are not accessible from the Internet .
o Locate control system networks and remote devices behind firewalls, and
isolate them from the business network.
o When remote access is required, use secure methods, such as Virtual Private
Networks (VPNs), recognizing that VPNs may have vulnerabilities and should
be updated to the most current version available. Also recognize that VPN
is only as secure as the connected devices.
CISA reminds organizations to perform proper impact analysis and risk
assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices
on the ICS webpage on us-cert.gov . Several recommended practices are available
for reading and download, including Improving Industrial Control Systems
Cybersecurity with Defense-in-Depth Strategies .
Additional mitigation guidance and recommended practices are publicly available
on the ICS webpage on us-cert.gov in the Technical Information Paper,
ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation
Organizations observing any suspected malicious activity should follow their
established internal procedures and report their findings to CISA for tracking
and correlation against other incidents.
CISA also recommends users take the following measures to protect themselves
from social engineering attacks:
o Do not click web links or open unsolicited attachments in email messages.
o Refer to Recognizing and Avoiding Email Scams for more information on
avoiding email scams.
o Refer to Avoiding Social Engineering and Phishing Attacks for more
information on social engineering attacks.
No known public exploits specifically target these vulnerabilities.
- --------------------------END INCLUDED TEXT--------------------
You have received this e-mail bulletin as a result of your organisation's
registration with AusCERT. The mailing list you are subscribed to is
maintained within your organisation, so if you do not wish to continue
receiving these bulletins you should contact your local IT manager. If
you do not know who that is, please send an email to email@example.com
and we will forward your request to the appropriate person.
NOTE: Third Party Rights
This security bulletin is provided as a service to AusCERT's members. As
AusCERT did not write the document quoted above, AusCERT has had no control
over its content. The decision to follow or act on information or advice
contained in this security bulletin is the responsibility of each user or
organisation, and should be considered in accordance with your organisation's
site policies and procedures. AusCERT takes no responsibility for consequences
which may arise from following or acting on information or advice contained in
this security bulletin.
NOTE: This is only the original release of the security bulletin. It may
not be updated when updates to the original are made. If downloading at
a later date, it is recommended that the bulletin is retrieved directly
from the author's website to ensure that the information is still current.
Contact information for the authors of the original document is included
in the Security Bulletin above. If you have any questions or need further
information, please contact them directly.
Previous advisories and external security bulletins can be retrieved from:
Australian Computer Emergency Response Team
The University of Queensland
Internet Email: firstname.lastname@example.org
Facsimile: (07) 3365 7031
Telephone: (07) 3365 4417 (International: +61 7 3365 4417)
AusCERT personnel answer during Queensland business hours
which are GMT+10:00 (AEST).
On call after hours for member emergencies only.
-----BEGIN PGP SIGNATURE-----
-----END PGP SIGNATURE-----