-----BEGIN PGP SIGNED MESSAGE-----
AUSCERT External Security Bulletin Redistribution
Advisory (icsa-19-330-02) ABB Relion 650 and 670 Series
27 November 2019
AusCERT Security Bulletin Summary
Product: ABB Relion 650 and 670 Series
Operating System: Network Appliance
Impact/Access: Denial of Service -- Remote/Unauthenticated
CVE Names: CVE-2019-18247
- --------------------------BEGIN INCLUDED TEXT--------------------
ICS Advisory (ICSA-19-330-02)
ABB Relion 650 and 670 Series
Original release date: November 26, 2019
1. EXECUTIVE SUMMARY
o CVSS v3 5.3
o ATTENTION: Exploitable remotely/low skill level to exploit
o Vendor: ABB
o Equipment: Relion 650 and 670 Series
o Vulnerability: Improper Input Validation
2. RISK EVALUATION
Successful exploitation of this vulnerability may allow an attacker to reboot
the device, causing a denial of service.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of Relion, a protection and control device, are
o Relion 650 series versions 184.108.40.206 and prior
o Relion 670 series versions 220.127.116.11 and prior
o Relion 670 series versions 18.104.22.168 and prior
o Relion 670 series versions 22.214.171.124 and prior
3.2 VULNERABILITY OVERVIEW
3.2.1 IMPROPER INPUT VALIDATION CWE-20
An attacker may use a specially crafted message to force the device to reboot,
which could cause a denial of service.
CVE-2019-18247 has been assigned to this vulnerability. A CVSS v3 base score of
5.3 has been calculated; the CVSS vector string is ( AV:N/AC:L/PR:N/UI:N/S:U/
o CRITICAL INFRASTRUCTURE SECTORS: Critical Manufacturing, Energy
o COUNTRIES/AREAS DEPLOYED: Worldwide
o COMPANY HEADQUARTERS LOCATION: Switzerland
Ilya Karpov, Evgeniy Druzhinin, and Victor Nikitin of ScadaX reported this
vulnerability to ABB.
ABB recommends that users apply the following or later versions at the earliest
o Relion 650 series version 126.96.36.199
o Relion 670 series version 188.8.131.52
o Relion 670 series version 184.108.40.206
o Relion 670 series version 220.127.116.11
Updates can be ordered by email at: email@example.com
ABB also recommends that these and other proper security practices and firewall
configurations be implemented to help protect a process control network from
attacks originating outside the network:
o Process control systems are physically protected from direct access by
o Process control systems have no direct connections to the Internet.
o Process control systems are separated from other networks by means of a
firewall system that has a minimal number of ports/services exposed.
o Process control systems should not be used for Internet surfing, instant
messaging, or receiving e-mails.
o Portable computers and removable storage media should be carefully scanned
for viruses before they are connected to a control system.
More information on recommended practices can be found in the ABB Cybersecurity
Deployment Guidelines for each product version.
ABB has not identified any workaround; however, firewall rules could be set to
block incoming traffic to Port 7001/TCP that originate from outside the
In the Relion 650 series Version 1.3, the SPA protocol over TCP/IP could be
disabled if it is not in use.
For more information, see the ABB Cybersecurity Advisory 1MRG027165
CISA reminds organizations to perform proper impact analysis and risk
assessment prior to deploying defensive measures.
CISA also provides a section for control systems security recommended practices
on the ICS webpage on us-cert.gov . Several recommended practices are available
for reading and download, including Improving Industrial Control Systems
Cybersecurity with Defense-in-Depth Strategies .
Additional mitigation guidance and recommended practices are publicly available
on the ICS webpage on us-cert.gov in the Technical Information Paper,
ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation
Organizations observing any suspected malicious activity should follow their
established internal procedures and report their findings to CISA for tracking
and correlation against other incidents.
No known public exploits specifically target this vulnerability.
- --------------------------END INCLUDED TEXT--------------------
You have received this e-mail bulletin as a result of your organisation's
registration with AusCERT. The mailing list you are subscribed to is
maintained within your organisation, so if you do not wish to continue
receiving these bulletins you should contact your local IT manager. If
you do not know who that is, please send an email to firstname.lastname@example.org
and we will forward your request to the appropriate person.
NOTE: Third Party Rights
This security bulletin is provided as a service to AusCERT's members. As
AusCERT did not write the document quoted above, AusCERT has had no control
over its content. The decision to follow or act on information or advice
contained in this security bulletin is the responsibility of each user or
organisation, and should be considered in accordance with your organisation's
site policies and procedures. AusCERT takes no responsibility for consequences
which may arise from following or acting on information or advice contained in
this security bulletin.
NOTE: This is only the original release of the security bulletin. It may
not be updated when updates to the original are made. If downloading at
a later date, it is recommended that the bulletin is retrieved directly
from the author's website to ensure that the information is still current.
Contact information for the authors of the original document is included
in the Security Bulletin above. If you have any questions or need further
information, please contact them directly.
Previous advisories and external security bulletins can be retrieved from:
Australian Computer Emergency Response Team
The University of Queensland
Internet Email: email@example.com
Facsimile: (07) 3365 7031
Telephone: (07) 3365 4417 (International: +61 7 3365 4417)
AusCERT personnel answer during Queensland business hours
which are GMT+10:00 (AEST).
On call after hours for member emergencies only.
-----BEGIN PGP SIGNATURE-----
-----END PGP SIGNATURE-----