-----BEGIN PGP SIGNED MESSAGE-----
AUSCERT External Security Bulletin Redistribution
Advisory (ICSA-19-136-01) Schneider Electric Modicon Controllers
17 May 2019
AusCERT Security Bulletin Summary
Product: Schneider Electric Modicon Controllers
Operating System: Network Appliance
Impact/Access: Unauthorised Access -- Remote/Unauthenticated
CVE Names: CVE-2018-7838
- --------------------------BEGIN INCLUDED TEXT--------------------
Schneider Electric Modicon Controllers
Original release date: May 16, 2019
All information products included in http://ics-cert.us-cert.gov are
provided"as is" for informational purposes only. The Department of Homeland
Security (DHS) does not provide any warranties of any kind regarding any
information contained within. DHS does not endorse any commercial product or
service, referenced in this product or otherwise. Further dissemination of this
product is governed by the Traffic Light Protocol (TLP) marking in the header.
For more information about TLP, see http://www.us-cert.gov/tlp/ .
1. EXECUTIVE SUMMARY
o CVSS v3 5.4
o ATTENTION: Exploitable remotely/low skill level to exploit
o Vendor: Schneider Electric
o Equipment: Modicon M580, Modicon M340, Modicon Premium, and Modicon Quantum
o Vulnerability: Use of Insufficiently Random Values
2. RISK EVALUATION
Successful exploitation of this vulnerability could allow an attacker to hijack
TCP connections or cause information leakage.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of Modicon products are affected:
o Modicon M580 firmware versions prior to Version 2.30
o Modicon M340 firmware, all versions
o Modicon Premium, all firmware versions
o Modicon Quantum, all firmware versions
3.2 VULNERABILITY OVERVIEW
3.2.1 USE OF INSUFFICIENTLY RANDOM VALUES CWE-330
The device has predictable TCP initial sequence numbers that allow attackers to
hijack TCP connections carrying unsecured communications.
CVE-2018-7838 has been assigned to this vulnerability. A CVSS v3 base score of
5.4 has been calculated; the CVSS vector string is ( AV:A/AC:L/PR:N/UI:N/S:U/
o CRITICAL INFRASTRUCTURE SECTORS: Multiple Sectors
o COUNTRIES/AREAS DEPLOYED: Worldwide
o COMPANY HEADQUARTERS LOCATION: France
David Formby and Raheem Beyah of Fortiphyd Logic and Georgia Tech reported this
vulnerability to NCCIC.
Schneider Electric reports the following mitigations:
o Modicon M580 firmware Version 2.80 is available for download. For more
information see Schneider Electric advisory SEVD-2019-134-03
o Modicon M340: currently, no fix is available.
Schneider Electric recommends that affected users set up network
segmentation and implement a firewall to block all remote/external
access to TCP ports.
Configure the Access Control List following the recommendations of the
user manual "Modicon M340 for Ethernet Communications Modules and
Processors User Manual," in the chapter titled "Messaging Configuration
Parameters," which is available here: https://
o Modicon Premium and Modicon Quantum
Set up network segmentation and implement a firewall to block all
unauthorized access to all TCP ports.
In December 2018, Schneider Electric reported that the Modicon Premium and
Quantum controllers reached the End of Commercialization life cycle. For more
information, please see Schneider Electric advisory SEVD-2019-134-03
NCCIC recommends users take defensive measures to minimize the risk of
exploitation of this vulnerability. Specifically, users should:
o Minimize network exposure for all control system devices and/or systems,
and ensure that they are not accessible from the Internet .
o Locate control system networks and remote devices behind firewalls, and
isolate them from the business network.
o When remote access is required, use secure methods, such as Virtual Private
Networks (VPNs), recognizing that VPNs may have vulnerabilities and should
be updated to the most current version available. Also recognize that VPN
is only as secure as the connected devices.
NCCIC reminds organizations to perform proper impact analysis and risk
assessment prior to deploying defensive measures.
NCCIC also provides a section for control systems security recommended
practices on the ICS-CERT web page. Several recommended practices are available
for reading and download, including Improving Industrial Control Systems
Cybersecurity with Defense-in-Depth Strategies .
Additional mitigation guidance and recommended practices are publicly available
on the ICS-CERT website in the Technical Information Paper,
ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation
Organizations observing any suspected malicious activity should follow their
established internal procedures and report their findings to NCCIC for tracking
and correlation against other incidents.
No known public exploits specifically target this vulnerability.
- --------------------------END INCLUDED TEXT--------------------
You have received this e-mail bulletin as a result of your organisation's
registration with AusCERT. The mailing list you are subscribed to is
maintained within your organisation, so if you do not wish to continue
receiving these bulletins you should contact your local IT manager. If
you do not know who that is, please send an email to email@example.com
and we will forward your request to the appropriate person.
NOTE: Third Party Rights
This security bulletin is provided as a service to AusCERT's members. As
AusCERT did not write the document quoted above, AusCERT has had no control
over its content. The decision to follow or act on information or advice
contained in this security bulletin is the responsibility of each user or
organisation, and should be considered in accordance with your organisation's
site policies and procedures. AusCERT takes no responsibility for consequences
which may arise from following or acting on information or advice contained in
this security bulletin.
NOTE: This is only the original release of the security bulletin. It may
not be updated when updates to the original are made. If downloading at
a later date, it is recommended that the bulletin is retrieved directly
from the author's website to ensure that the information is still current.
Contact information for the authors of the original document is included
in the Security Bulletin above. If you have any questions or need further
information, please contact them directly.
Previous advisories and external security bulletins can be retrieved from:
Australian Computer Emergency Response Team
The University of Queensland
Internet Email: firstname.lastname@example.org
Facsimile: (07) 3365 7031
Telephone: (07) 3365 4417 (International: +61 7 3365 4417)
AusCERT personnel answer during Queensland business hours
which are GMT+10:00 (AEST).
On call after hours for member emergencies only.
-----BEGIN PGP SIGNATURE-----
-----END PGP SIGNATURE-----